What do we mean by the term “pumped water system”? In this series of articles, we will be referring to systems that move ground water from a well to its intended point of use – the types of systems likely to be encountered by well drillers and other ground water professionals. We’ll start with a look at the heart of any pumped water system, the pump.
Water, and other fluids, can be moved in many ways. If water is above where you want it, gravity can get it to its destination. If you need to get it higher than where it is, you’ll need some sort of pump. There are ram pumps, piston pumps, gear pumps, diaphragm pumps, lift pumps, centrifugal pumps, etc., each having its own place in the sun – or under the ground, as the case might be.
Some are positive displacement pumps capable of moving relatively small amounts of fluids at very high pressures, way more than is needed in most water system applications. Others, like the centrifugal pump, don’t produce much pressure or lift, but can move very large amounts of water. However, if configured properly, as will be pointed out later, centrifugal pumps can produce a respectable amount of pressure.
There are four basic types of pumps commonly used in ground water applications. They are the straight centrifugal, the shallow-well jet pump, the deep-well jet pump and the submersible pump. All four types will be described in detail in the coming months. So that you can have a mental image of each, here are brief descriptions and pictures of typical examples of each. You also should know that all four types are variations of the basic centrifugal pump.
1. The straight end-suction centrifugal consists of a motor to provide the energy, an impeller to spin and accelerate the water, a volute to concentrate the water and build pressure, and a housing or case to contain the pressure and provide a place to attach the pipes to the pump. They are called “end suction” because the suction pipe is connected to the end of the pump opposite the motor. An end-suction centrifugal pump can draw water from as deep as 20 feet.
2. A shallow-well jet pump is an end-suction centrifugal pump with an attachment on the front of the pump housing, which boosts the pressure. The attachment, called a jet assembly, uses a venturi to convert some of the energy from the centrifugal portion of the pump into pressure, both positive pushing pressure and negative vacuum-producing pressure. A shallow-well jet pump can draw water from as deep as 25 feet.
3. A deep-well jet pump is similar to a shallow-well jet, but the jet assembly is located down in the well where it pushes the water to the surface instead of pulling it. As you will learn later, there are natural laws governing the depth from which we can pull water to the surface, so having a pump that pushes the water allows us to pump from much deeper wells. A deep-well jet pump can pump from as deep as 150 feet.
4. A submersible pump has the same parts as a straight centrifugal pump, but the parts all are small enough in diameter, even the motor, to fit into a well. Although there are single-impeller submersible pumps used for special applications, most submersible pumps have more than one impeller/volute assembly. Each impeller/volute assembly is called a stage, and each stage adds to the pressure produced by the one before it. For vary deep wells, it is not uncommon to have more than 50 stages. A multi-stage submersible pump can pump from significantly more than 1,000 feet deep.
The other major component at the wet end of a centrifugal pump (as distinguished from the motor end) is the pump housing, called a volute in an end-suction centrifugal, and a diffuser in a submersible or jet pump. Its purpose is to contain the water pumped by the impeller and to direct it to the pump discharge or to the inlet of the next impeller in a multi-stage pump.
The closeness of the fit between the inlet of the impeller and the pump housing affects the pump’s performance. If there is too much clearance, some of the water that has been pumped through the impeller simply will leak around the impeller and back to the inlet, reducing the discharge pressure and the amount of water delivered. Not only is this fit an important element in the design and manufacture of a pump, it can deteriorate during normal usage, due to corrosion or erosion of the pump’s impeller and housing, decreasing a pump’s performance.
Next month, we will continue this discussion on pump basics with a look at how centrifugal pumps make pressure. ’Til then ….